Testing Your Emergency Phones
Emergency phones serve a very important purpose, but if you do not regularly test your phones, they may not be code compliant or even function safely and effectively. This blog covers how to easily test your phones to ensure functionality and compliance.
As a property manager, we are sure that you are aware that it is required by law that you provide emergency phones within your elevators. Emergency pool phones are additionally required by law in many states. On top of this, many property managers host additional emergency phones on their properties including areas such as sidewalks, gyms, parking garages and stairwells, as they recognize the benefits of extra safety and reduced liability that these can provide. Our point here is that if you’re in the property management industry, you likely have at least one emergency phone on your property. You may think by simply having the emergency phone there that you are adhering to laws or providing the needed protection for your property, but there is always room for errors and malfunctions when it comes to technology, and if certain aspects of your emergency phone aren’t working correctly, this can lead to both code compliance and safety failures. This is why it is so important to regularly test your emergency phones. We know, we know, you’ve already got a lot on your plates. Luckily the testing process is a quick and easy one. See below for just how to do so.
Find out how to improve safety and reduce costs at your property
Our best-in-class emergency phone + monitoring solutions provide peace of mind and are backed by decades of expertiseLearn More
Elevator Emergency Phones:
Your state enforces ASME A17.1 which requires a working emergency telephone or intercom for elevator emergency communications. The steps below will help you determine whether your emergency phone complies to this code.
1. Activate two or more elevator phones at the same time in order to determine that phones are able to hold a two-way conversation with emergency operator(s) simultaneously. If only one or none of the calls go through, one call is disconnected once the second one is made, the phones do not dial out or the parties cannot hear each other once the call is placed, this portion of the test is failed.
2. Ask the emergency phone operator if he/she is able to identify your cab numbers and location. If they are unable to do so, the emergency phone has failed this portion of the test.
3. Use the emergency responder phone (usually located on the main egress level, in the fire control room or at a guard station) to call and test the on-site responder’s ability to directly call back into the elevators without delay. If the elevator phones cannot be called back properly, this indicates failure.
If all above components function properly, you can rest easy knowing that your emergency phone will perform as expected in an emergency situation and complies to code.
Pool and Other Emergency Phones:
The process for testing your other emergency help phones is similar to that of testing your emergency elevator phones, the main difference being that you do not need to test to see if phones are working simultaneously as you do for separate elevator cabs. See the steps below:
1. Initiate a call from your elevator phone. If you are unable to connect, your emergency phone has failed this portion of the test.
2. If connected, tell your operator that you are performing a test and ask if they are able to hear you well. If they are able to do so, you are able to move on to the final portion of the test.
3. Ask the operator if they can identify your location. For ADA compliance, the most important requirement is that the emergency operator answering the call must be able to determine the exact location of the caller without the caller telling them. If the operator is unable to do so, the phone is not ADA compliant.
After performing a test, if any of your phones are not working correctly, be sure to contact the appropriate specialist as soon as possible so that they can assess the problem and provide a customized solution. If you are a Kings III customer, full maintenance is likely included in your service package, so please do not hesitate to call. For more information regarding code compliance in regards to your elevator, download our free guide, “Understanding Elevator Emergency Communication Code Compliance.”
Not all on-site emergencies take place during regular working hours, but that doesn't make them any less important to address. Here's how property managers can effectively respond to property emergencies occurring after-hours without an unrealistic, burdensome workload.
If you rely on tenants' smartphone use as an on-site emergency response, you're opening up some liability issues when it comes to property safety. Here's what you need to know.
Because your fitness center could be one of the more popular amenities on your property, it certainly brings a need for a plan to manage risks that can occur. If you haven’t already, it’s important to establish life safety and emergency response practices specifically designated for the area. Here are some of the essentials.
Elevator Communications and Data Connection Requirements: Properly Evaluating Security Risk, Reliability and Encumbrances
There’s a lot to consider when thinking about the new elevator emergency communication code requirements. Deciding to use your own network creates a long checklist and more work for you. Granting a third party vendor access to your network is an option but has risks. Here are a few things to consider when making your decision.
As part of Building Safety Month, we’re taking a look at some fundamental property crime statistics that all property managers should know, adding in some of our own crime prevention and crime response tips.
We have found as an emergency pool phone provider that there are multifamily communities unaware that their current pool phone service is actually using a deactivated cell phone. Depending on the authority having jurisdiction (AHJ), this often does not pass inspection for several reasons. This puts both property managers and their tenants at risk. Learn why.
Kings III equipment has been approved for the use of FirstNet, built by AT&T, which is a long-term evolution (LTE) network that gives first priority to first responders and other public safety personnel. Learn more here.
After a rigorous review process, Kings III’s emergency phone host control panel, the M90, is now FirstNet Ready™ and ready for use on FirstNet®, a public safety network. Learn items of note.
See how Kings III's emergency dispatch center was able to run as-usual during the mass Texas power outages and how we're prepared to do so in any outage.
Kings III makes it easy as a single point-of-contact for all your emergency response needs. With expertise in line connectivity, compliance codes, equipment maintenance and safety protocol, we offer the total package.